During the latest product approval, also the pressure rating of Agru’s SDR 11 and SDR 9 FM approved HDPE pipes and fittings product range has been increased significantly. This brings extensive cost benefits during installation compared to other FM approved HDPE piping systems and makes AGRU FM approved HDPE piping systems the first choice for reliable, underground installed firefighting systems.
There are two complete AGRULINE product ranges for FM 1613 approved underground firefighting systems available: FM approved per approval standard 1613 for 218 psi (15 bar, SDR11 ), and for 250 psi (17,5 bar, SDR9). This pressure designation means maximum operating pressure for firefighting systems, at 23 °C. It is calculated and tested that all the system components can handle 4 times of the specified pressure in case of а water hammer without any failure.
Many industrial companies operate special fire-fighting systems to prevent property losses. A complete fire-fighting system needs underground pipelines (main lines) with easily accessible fire hydrant connections. The material PE 100-RC is slowly advancing to one of the most used materials for fire-fighting applications. AGRU offers one of the complete product ranges of FM approved HDPE (PE 100-RC) pipes and fittings for underground fire service mains worldwide. Customers from various business fields trust into AGRUs’ high-quality products and its years of experience. Both of it leads to a perfect solution. That makes AGRU the reliable partner when it comes to preventing property loss.
The water supply of а fire protection system is often considered as the most critical component of the system. Moving the water from it’s source to the entrance of the building, is the function of underground fire protection piping. This piping system must be extremely reliable to withstand internal and external stresses over long periods of time. РЕ 100-RC pipes and fittings can bе welded together homogeneously by butt-fusion welding or electro-fusion welding. The welded joints are as strong as the pipe itself, providing а continuous leak-tight system. On the other hand РЕ 100-RC pipes do not corrode or incrustate. This is а key point as in case of а fire emergency valves will Ье opened immediately and if pipes are corroded or incrustated – particles may bе flushed and clog the sprinklers inside the building.
FM APPROVED HDPE PIPING SYSTEM FOR THE UNDERGROUND FIRE PROTECTION SYSTEM OF THE DUBAI METRO DEPOTS
The security within the Metro depots will be ensured by an underground fire protection system that is equipped with AGRU pipes made out of polyethylene. The piping system was delivered by AGRU’s exclusive distributor BMC Gulf, who received an order from the project contractor. Additionally, BMC Gulf was asked to supply the appropriate welding machines and to take care for the project supervision at the construction site. Concerning welding machines fully automated CNC machines with data recording from WIDOS were selected. For the welding and installation Certified HDPE Pipe Welders (according to GW330, DVGW standard) from the SKZ German Plastics Center (UAE) were employed.
Dubai is booming. In 2008, already two million people have been living on an area comprising not more than 4,000 km2, and this development won’t stop regarding the yearly population growth of about 8%. For visualization of the enormous space problem in this country, compare this: In Austria currently eight million inhabitants are living on an area that is 20 times bigger than Dubai. Whereas the big construction projects don’t seem to come to an end, the infrastructure has not been adapted to the growing demands so far.
Since 2006, a project is in preparation that will eliminate going by car as sole possibility for being mobile: Dubai’s 76 km, fully-automatic Metro system. The Dubai Metro is an unprecedented project in the Middle East region. The increasing traffic, mainly caused by business and tourism, and also the pollution burden has been solved by September 9, 2009. Then, the first 52 km of the „Red Line“ – a metro that goes partly underground, partly on elevated viaducts – has been finished.
The security within the Metro depots will be ensured by an underground fire protection system that is equipped with AGRU pipes made out of polyethylene. The piping system was delivered by AGRU’s sales partner BMC Gulf, who received an order from the subcontractor Build Force. Additionally, BMC Gulf was asked to supply the appropriate welding machines and to take care for the project supervision at the construction site. Concerning welding machines fully automated CNC machines with data recording from WIDOS were selected. For the installation certified welders (acc. to DVGW standard GW 330) from the SKZ Training Centre UAE were employed.
IMPORTANT FACTS ABOUT THE PROJECT:
• 7.5 km FM approved HDPE pipes (OD 110, 125, 160, 200, 225, 250 and 280 mm)
• FM approved HDPE injection moulded fittings (tees, bends, reduced parts, etc.)
• FM 1613 approved components
• Client: Roads & Transport Authority Dubai (RTA)
• Main Contractor: JT Metro JV
• Subcontractor Piping: Build Force LLC
AGRU’s HDPE piping system will serve the depots with water for the underground fire protection system. In these stations, all trains are stored when they are not in use or maintained. Only FM 1613 listed piping components class 175 from AGRU have been applied, which guarantees high quality and safety. Furthermore, the many advantages of HDPE compared to other materials resulted in the selection of a FM listed HDPE plastics system:
• corrosion resistance
• easy installation
• no need for maintenance
FM Global (= Factory Mutual) is the world’s largest commercial and industrial property insurance and risk management organization specializing in property protection.
FM Approvals of industrial products and services are globally recognized and respected. The FM APPROVED mark assures that a product or service has been objectively tested in accordance with national and international standards. The customers rely on FM APPROVED products and services to support property loss prevention.
AGRU as well as AGRU-FRANK fulfils the strict demands of the FM institute and has now an approval for PE 100 heating element butt welding-, electro fusion fittings and pipes according to FM Class Number 1613 „Polyethylene (PE) Pipe and Fittings for Underground Fire Protection“. The FM Approval is currently issued for the dimension range of Ø63 up to Ø400 mm in SDR 11. In future, this quality will be secured through an annual third party audit by FM. The pipes and fittings are approved for a maximum operating pressure of 12 bar/175 psi according to FM Class Number 1613.